06/30/2016 - 08:56
The Pumps UK service division were approached by a local retirement village to assist in an ongoing pumping issue they had. The site had a very large sewage chamber with two old Calpeda sump pumps installed...
06/16/2016 - 16:00
Pumps UK Service were approach by Dartford FC, a local football club to us, and they informed us that their pump which supplies water to the sprinklers for the main football pitch had failed and they needed a replacement urgently.
04/07/2016 - 09:14
We recently attended a site in Trevor Square, London to overhaul a Wilo DPN twin circulator. Once we had dismantled it we found that the internals of the pump had worn out beyond repair...
03/16/2016 - 14:39
We were asked by a client to remove their old direct driven Crane pump which was used to circulate the chilled water and to install a new Lowara twin pump set. Upon visiting the client’s site we noticed it was currently running with only with 1 pump which greatly hindered performance and efficiency.
02/01/2016 - 14:43
Pumps UK was contacted by a client to replace an old set of belt driven Pullen pumps in their office block in Aldgate, London.
We decided that a suitable replacement for the old Pullen pumps would be a set of direct drive circulators from Grundfos. After we had taken out the old pumps we had to build a bespoke frame simply because the pumps were located on the roof top plant room and meant that we needed to transport the pumps up the stairs. Our in house engineer fabricated a frame which had a runner and installed it on the plant room’s stairs.